1766 UM001 EN P PDF
Publication UMA-EN-P – November Table of Contents . User Manual UM to assign an IP address to the MicroLogix. controller. Publication INC-EN-P – October Important . Manual UM .. publication UM, for more information on surge suppression. rm_-en-p – Free ebook download as PDF File .pdf), Text File .txt) or read book online for free. Document Number IN UM
|Published (Last):||8 June 2014|
|PDF File Size:||19.1 Mb|
|ePub File Size:||3.1 Mb|
|Price:||Free* [*Free Regsitration Required]|
Do not touch the connector pins or other sensitive areas.
Scripting must be enabled to use this site.
However, because of the variety of applications and environments where analog controllers are installed and operated, it is impossible to ensure that all environmental noise will be removed by the input filters. Output group to output group isolation Verified by one of the following dielectric tests: Replace the cover as shown below.
No patent liability is assumed by Rockwell Automation, Inc. Run the ground connection from the ground screw of the controller to the ground bus prior to connecting any devices. The examples and diagrams in this manual are included solely for illustrative purposes. For more information, contact your local distributor or Rockwell Automation representative, or visit http: Mount your DIN rail.
The analog output can support a voltage function as shown in the following illustration. Install your controller using these installation instructions. Failure to remove the strip before operating can cause overheating.
Vertical mounting is not supported due to thermal considerations. You can also contact a special Customer Support number for initial help in getting your product up and running.
Be sure that the area is nonhazardous before proceeding. This could cause an explosion in hazardous location installations. When you connect or disconnect the battery an electrical arc can occur. A flat-blade screwdriver is required for removal of the controller. MicroLogix Instruction Set Reference Manual RM A reference manual that contains data and function files, instruction set, and troubleshooting information for MicroLogix Follow these steps to connect the replaceable battery.
It must be mounted within an enclosure that is suitably designed for those specific environmental conditions that ym001 be present and appropriately designed wn prevent personal injury resulting from accessibility to live parts. Use only the following communication cables in Class I, Division 2 hazardous locations. The interior of the enclosure must be accessible only by the 11766 of a tool.
At this level transient voltages are controlled and do not exceed the impulse voltage capability of the product’s insulation. DIN rail mounting dimensions are shown below. Follow these guidelines when you handle this equipment: Replacing the battery when the controller is powered down will lose all user application memory.
B mm 7.
1766-IN001 – Rockwell Automation
Store the equipment in appropriate static-safe packaging when not in use. Locate your controller as far as possible from power lines, load lines, and other sources of electrical noise such as hard-contact switches, relays, and ac motor drives. Power supply inrush current V AC: For more information on proper grounding guidelines, refer to the Industrial Automation Wiring and Grounding Guidelines, publication Holding the controller, pry downward on the latch until the latch locks in the open position.
You must provide a Customer Support case number call the phone number above to obtain one to your distributor in order to complete the return process. Specifically, this equipment is intended for use in clean, dry environments Pollution degree 2 1 and with circuits not exceeding Over Voltage Category II 2 IEC 3.
Make sure that the MicroLogix system is properly grounded. The Belden cable has two signal wires black and clearone drain wire, and a foil shield.